Features & Specifications
Wall Mounted Cabinets: Maximum storage in a compact size. Wall Mounted Cabinets will hold up to 24 gallons of flammable liquids without taking up valuable floor space. Furnished with brackets for easy wall mounting or can be placed on a bench top. Equipped with adjustable shelves which can be positioned to meet your specific needs.
Stackable Cabinets: These cabinets are designed to be used as a single cabinet, to fit on top of standard 30 gallon cabinets or on top of each other. Ideal for segregating flammables or to increase the capacity of your current cabinet.
|Dimension (H x W x D) (in)
|24"H x 43"W x 18"D
|No. of Doors
|Self-Latch Standard Door
|No of Shelves
|Shipping Weight (lbs)
|Complies with current OSHA regulations, FM-Factory Mutual Approved, NFPA - Designed in accordance with specifications set forth by the National Fire Protection Association
|15 Year Limited Structural Warraty
All Securall cabinets are built to the highest quality specifications. Whether you are storing dangerous flammable chemicals or you need a cabinet for heavy industrial tools, we have the perfect cabinet for your needs. If you have a special situation that requires a customized design, we will welcome the opportunity to work with you to provide a safe storage solution. All cabinets comply with current OSHA regulations and are designed in accordance with the standards of NFPA Code 30. Popular models are FM Approved.
18 GAUGE DOUBLE WALL CONSTRUCTION & SEAMED JOINTS
Securall Safety Cabinets have Structurally Reinforced 18-Gauge Double Wall All Welded Construction throughout.
DOUBLE WALL CONSTRUCTION WITH 1 ½” AIR SPACE
Securall cabinets have Double Wall Construction with 1 ½" Air Space throughout the cabinet design.
2" DEEP LEAK PROOF SILL
Securall cabinets are built with an OSHA compliant leak proof sill 2" Deep to prevent leakage in the event of accidental spills.
NON-SPARKING , 3-POINT, SELF-LATCHING DOORS
Each Securall cabinet is outfitted with FM required Non-Sparking, 3-Point, Self-Latching door(s) for safe and complete closure every time.
SELF-CLOSING MECHANISM (IF INSTALLED) SEGREGATED FROM HAZARD AREA
Securall Self Closing Cabinet - Self closing mechanism segregated from interior of cabinet and contents stored.
FUSIBLE LINK ASSEMBLY ON SELF-CLOSING MODELS
Self-Closing cabinets come with Fusible Link Assembly. Link melts at 165 F for automatic closure in case of fire. Self closing mechanism segregated from hazard area.
STATIC GROUNDING CONNECTION
All Securall cabinets come ready with an FM defined static ground connection, comprised of a NFPA compliant 5/16 - 18 x ½” Zinc Plated Grounding Bolt.
LARGE WARNING LABEL
Securall cabinets have a Large Warning Label to identify the type of material stored within the unit. Also available in French and Spanish.
ADJUSTABLE LEVELING LEGS
Securall cabinets are equipped with four adjustable Zinc Plated Leveling Legs for placement on uneven surface areas.
FLUSH MOUNTED LOCKING HANDLE
All Securall safety cabinets come standard with a Flush Mounted Locking Handle for smooth finger-tip operation.
FULL LENGTH, HEAVY-DUTY PIANO HINGES
Securall double-wall doors are secured to unit on full length, Heavy-Duty Piano Hinges for maximum security and limited vapor release.
The interior and exterior finish consists of an aliphatic polyurethane finish. This polyurethane coating has chemical properties to withstand salt spray, chemical rub, fading due to UV exposure, and other tests performed to epoxy paints. Urethane is more durable under conditions when moving items in and out of the cabinet as it resists chipping and peeling. Unless some other color is specified, cabinets will ship in designated standard color. For custom colors, customer must provide a paint chip.
Flammable & Combustible Classes
NFPA FLAMMABLE & COMBUSTIBLE CLASSES
|<73°F (22.8°C) and <100°F (37°C)
|100° F (37.8° C) ≤ FP < 140° F (60° C)
|140° F (60° C) ≤ FP < 200° F (93° C)
|200° F (93° C) ≤ FP
9.5.1 The volume of Class I, Class II, and Class IIIA liquids stored in an individual storage cabinet shall not exceed 120 gal (460 L).
9.5.2 The total aggregate volume of Class I, Class II, and Class IIIA liquids in a group of storage cabinets shall not exceed the maximum allowable quantity of flammable and combustible liquids per control area based on the occupancy where the cabinets are located.
* NFPA 30 Flammable and Combustible Liquids Code, 2011 Edition. Section 9.5.1, 9.5.2